12/01/2018 Neuron control units have a wide range of applications. Today, we bring you an example of an economical heat pump system made by the TVK servis, s. r. o. company, which uses the Neuron S103 as a control unit.
The goal of the TVK servis s.r.o. company was to decrease buying cost of heat pumps for family houses. For this purpose, a heat pump assembly was designed, consisting off commercially available outdoor inverter unit and other components - plate heat exchanger, circulator pump, expansion tank, backup heat source, water filter, three-way valve and armatures.
As a control unit, the Neuron S103 was used. This model features following I/O configuration:
- 4x digital input
- 4x digital output
- 1x analog input
- 1x analog output
- 1x RS485 bus (Modbus protocol)
- 1x 1-Wire bus
Inputs and outputs are utilized in a following way:
- digital inputs: external thermostat
- digital output:
- heat pump switch
- three-way valve control
- water heater's cartridge heater switch
- bivalent heat source (electric boiler)
- analog input: flow thermometer
- analog output: heat pump output regulation
- RS485 bus (Modbus protocol): energy meter measuring heat pump power consumption
- 1-Wire bus: a set of 1-Wire temperature sensors measuring outside temperature, water heater temperature, reversing valve temperature, temperature behind the backup heat source and temperature behind the coolant/water exchanger
From software point of view, the Mervis software platform is used. In the Mervis runtime, the user can manage regular functions of the heat pump, i.e. equitherm management, heating time schedule, hot water heating priorities, diagnostics etc. The temperature and water flow measurements then allow the heat pump's coefficient of performance (COP). Mervis DB database is used for logging parameters used for example for fine-tuning the equitherm graph. Users have the option to use web interface. Service technicians of the TVK servis company then can access the system regulator remotely through a proxy server for diagnostics, software updates and other maintenance tasks.
Temperature measurement output graph
Web interface for control and monitoring of the heat pump.
According to the company, the complete system achieved all goals. Currently, two installations are in operation - one with a Sinclair inverter unit and one with a Mitsubishi unit. Both systems are fully functional and compared to en bloc systems offered on the market, TVK servis company solution is more financially accessible for customers. As to further development, the TVK servis is currently performing tests of remote system access through the MS Azure cloud service.
Distribution box with the Neuron S103 unit installed
Distribution box and bivalent electric boiler (on the left)
Coolant/water exchanger and three-way valve
Flow temperature meter connected to control unit's analog input
Our partsUniPi Neuron S103
More than 20 items in stock
1-Wire Temperature Sensor
More than 20 items in stock
Less than 20 items in stock